1. Correct use of laminar flow room: the operating table shall be arranged as close as possible to the appropriate place of laminar flow ceiling net, and all operation steps shall be as close as possible to the corresponding place of laminar flow ceiling net to prevent sterile package at the return air outlet. Infection operation shall be arranged in the operation room with negative pressure laminar flow as far as possible, and special disinfection shall be carried out in case of special operation. The operation shall be carried out according to the three channel line: the entrance and exit of medical personnel, the entrance and exit of patients and the exit of dirt are the access lines designed for the laminar flow operating room.
2、保持清潔效果：采用手術室凈化空調系統應該持續使用24 h，培養空氣細菌合格次數打2次后投入使用。手術前半小時將層流空調系統打開，接臺手術需相隔15 min，保證空調系統持續運轉。在手術前期要采用500 mg/L的含氯消毒液濕式將有關器材的血跡灰塵清理干凈。對于初效、中效過濾器更換周期為6個月/次，過濾器1～2年/1次?；仫L口1周/1次，這樣才能保證使用器材的清潔效果。
2. Keep the cleaning effect: the operating room purification air conditioning system should be used for 24 hours, and the air bacteria should be cultured for 2 times before being put into use. Turn on the laminar flow air conditioning system half an hour before the operation, and the next operation needs to be separated by 15 minutes to ensure the continuous operation of the air conditioning system. In the early stage of operation, 500 mg / L chlorine containing disinfectant shall be used to wet clean the blood and dust of relevant equipment. For primary and medium efficiency filters, the replacement cycle is 6 months / time, and the filter is 1 ~ 2 years / time. Return air outlet once a week, so as to ensure the cleaning effect of equipment.
3. Equipment protection: in the early stage of operation, it is usually necessary to control the indoor temperature at an unsteady value and ensure that the air conditioner operates for 24 hours, or turn it on half an hour before operation according to its own situation. Clean the primary filter screen and air outlet once a week to avoid pollution. The replacement of medium efficiency and filter screen shall be carried out according to the air culture.
The temperature regulation in the operating room is very important, and there should be cold and heating regulation equipment. The air conditioner shall be set in the upper roof, the room temperature shall be kept at 24 ~ 26 ℃, and the relative humidity shall be about 50%. The general operating room is 35 ~ 45 m2, and the special room is about 60 m2, which is suitable for cardiopulmonary bypass, organ transplantation, etc; The area of small operating room is 20 ~ 30 ㎡.
The above highlights are provided for you by the air purification project. The air purification project is specially for various operations that should pay attention to the overall energy consumption after the implementation of operating room purification and use optimized ways to save energy. Please continue to pay attention to our website for more highlights: http://www.nexregen.com